BlogVaillant Eco Tec error / fault code F.54 and F.28
Vaillant Eco Tec error / fault code F.54 and F.28
posted on 22 Jan 2017
If your Vaillant boiler is showing error code F.28 in very cold weather it is most likely that your condensation pipe is frozen outside. Pour hot water over the pipe and reset the boiler (Or turn it off and on at the spur switch). If possible put some pipe insulation on condensate pipework. Condensate pipework will be in white, grey or black plastic and around 21mm or 35mm in size.
I got called to Vaillant EcoTec Plus 825 with intermittent problems with ignition. I went to fault history to check errors that boiler was showing at the time of failure. This can be done in diagnostic menu. I found two codes: F.54 and F.28 in the fault history. Both codes are gas supply related and can show up together. According to Vaillant 825 manual:
F.54 – fault in the gas supply. Insufficient gas supply to operate the boiler.
F.28 – failure during start up. Ignition unsuccessful. Possible causes:
Gas meter defective or gas pressure monitor has triggered, air in gas, gas flow pressure too low, thermal isolator device (TAE) has triggered, condensate duct blocked, incorrect gas restrictor, incorrect spare part gas valve, fault on the gas valve, multiple plug on PCB incorrectly plugged in, break in cable harness, ignition system (ignition transformer, ignition cable, ignition plug, ignition electrode) defective, ionisation current interrupted (cable, electrode), incorrect earthing of product, electronics defective
Fault – check gas route – in connection with F.54 and F.28. This fault will also display a service required symbol on boiler display. (Spanner symbol). To remove spanner symbol a successful gas family check at installer level is required.
When I got to site boiler was igniting and not showing any errors. Quick checks of gas pressures on the boiler and at the meter confirmed faulty part. Gas supplier got contacted and gas supply was repaired the same day. This time it turned out to be a problem on gas meter / gas supply side not the boiler itself.
If your Vaillant boiler is suffering from F.28 and F.54 errors you can contact me through this website to arrange for a repair. I cover most of London.
If your boiler is showing error code F.28 on it’s own please make sure that your gas supply is on or your pre paid meter is in credit.
‘Plumber to fix leaking boiler in SE19’ – boiler repair blog
I got called to diagnose and repair a suspected boiler leak in SE19, Crystal Palace. The client actually used the phrase ‘Plumber to fix a leaking boiler in SE19’ to find me on Google. When I got to site I was met with this massive leak coming from the boiler pressure relief valve that has […]
12 January 2020
Vaillant Eco Tec ‘Con’ error code
If your boiler is showing ‘Con’ message on main display it means that your main PCB or possibly display PCB has failed and will need to be replaced. ‘Con’ message means that there is a communication error between main board and display board. Both boards are connected directly with pin connectors so that takes out […]
11 January 2020
Baxi error code E133 – ignition lockout
E133 error code on a Baxi/ Potterton / Main boiler is an ignition lockout fault code. This error code that covers a wide range of possible faults connected to gas and igniton. In most cases you will need to contact a competent boiler repair engineer but there are some steps you can take yourself before […]