BlogAriston E Combi 24 not igniting in the morning – intermittent fault
Ariston E Combi 24 not igniting in the morning – intermittent fault
posted on 19 Mar 2017
Owner of this Ariston E Combi 24 described the fault as follows:
boiler does not ignite in the morning and requires multiple resets to get it going
once boiler starts it seems to be working fine
boiler fails to ignite after longer periods of no use
When I got to site I noticed that boiler would take 2-3 attempts at ignitions with 2nd or 3rd one being successful and boiler would not go into lockout while I was on site. After testing rectification, gas pressures and combustion I got satisfactory results for all of those. I suspected problem with either gas meter regulator or one of the main components of the boiler not connected to rectification or ignition. Gas meter supply and governor checks confirmed that in fact the problem was on the boiler side. While testing all of the above I managed to witness boiler going into lock out.
This early Ariston E Combi does not have a digital display and error codes are communicated through number of combinations of led temperature display. Below is a picture of Flame Lift / Ignition lock out error code with 3 temperature led illuminated together with red ignition error led illuminated below on the right hand side.
Close up of the error code below
Since gas supply has been operating correctly, combustion and rectification was giving correct results that left only one major component that could have been faulty. Faulty part got replaced at next visit and boiler is now working correctly.
Boiler igniting correctly and displaying actual operating temperature instead of an error code below.
I also noticed pressure going up to around 3bar while system was heating up pointing to flat expansion vessel. Client is supposed to book a second service visit to rectify this problem.
‘Plumber to fix leaking boiler in SE19’ – boiler repair blog
I got called to diagnose and repair a suspected boiler leak in SE19, Crystal Palace. The client actually used the phrase ‘Plumber to fix a leaking boiler in SE19’ to find me on Google. When I got to site I was met with this massive leak coming from the boiler pressure relief valve that has […]
12 January 2020
Vaillant Eco Tec ‘Con’ error code
If your boiler is showing ‘Con’ message on main display it means that your main PCB or possibly display PCB has failed and will need to be replaced. ‘Con’ message means that there is a communication error between main board and display board. Both boards are connected directly with pin connectors so that takes out […]
11 January 2020
Baxi error code E133 – ignition lockout
E133 error code on a Baxi/ Potterton / Main boiler is an ignition lockout fault code. This error code that covers a wide range of possible faults connected to gas and igniton. In most cases you will need to contact a competent boiler repair engineer but there are some steps you can take yourself before […]