Boiler reapir blog – Main combi 24he with intermittent flame failure
*** You are breaking the law if you are working on gas appliances and you are not competnet to do so and Gas Safe Registered. Do not attempt any work on gas appliances unless you are qualified and Gas Safe registered. If your boiler suffers from this problem please contact a qualified and Gas Safe Registered enigneer to repair your boiler. This blog is intented to help out fellow engineers only. No responsibility can be taken for any injury caused by illegal gas work***
I got a call to repair an intermittent fault on Main 24HE combination boiler. Information I was given was that boiler had been intermittently falling to flame failue (middle of 3 led lights flashing on the boiler) over longer period of time and that recently it had started to become more frequent.
Generally flame failure can be caused bya number of issues such as:
rectification electrode faulty or failling
ignition electrode failing
ingition or rectification wirign faulty
faulty gas valve
faulty fan or weak fan
faulty air pressure switch
faulty PCB (Printed circuit board)
All of the above can cause an intermittent fault but some components are much more likely to be intermittent than others. With intermittent faults my first port of call would be as follows: PCB, air pressure switch, electrodes, weak fan. If boier did not start at all then I would start by looking at fan or gas valve.
Fault finding logic in this case would be to follow boilers sequence to try to establish at which stage boiler fails when it does go into the ‘flame failure’
Sequence of Main 24HE is as follows:
call for heat from thermostat or call for hot water
air pressure switch makes contact and send singal that fan is OK to PCB
PCB send signal to gas valve to open
Ignition electrodes get voltage to spark ignition (from spark generator controlled by PCB)
Burner ignites and flame sensing electrode send singal to PCB that flame is OK
What I was looking at is stage at which boiler fails. When on site boiler went into ‘flame failure’ around 70% of the time so it was relatively easy to see what was happening. In this instance what was happening was:
call for heat or hot water
boiler fails to ignite, there is no sound of sparking
From that information I knew that I can rule out follwoing components:
sensing electorde – as boiler does not ignite
fan – fan starts and differential pressure is correct
Whaterver componet is failing it will be after the fan. I will be looking at compotnets and testing them in following order:
air pressure switch
My tests confirmed faulty component quickly and boiler got repaired the same day.
Have you come accross similar fault on Main / Baxi / Potterton boilers? What was the outcome? Let me know.
I recorded a short video from this repair that you can watch below.
‘Plumber to fix leaking boiler in SE19’ – boiler repair blog
I got called to diagnose and repair a suspected boiler leak in SE19, Crystal Palace. The client actually used the phrase ‘Plumber to fix a leaking boiler in SE19’ to find me on Google. When I got to site I was met with this massive leak coming from the boiler pressure relief valve that has […]
12 January 2020
Vaillant Eco Tec ‘Con’ error code
If your boiler is showing ‘Con’ message on main display it means that your main PCB or possibly display PCB has failed and will need to be replaced. ‘Con’ message means that there is a communication error between main board and display board. Both boards are connected directly with pin connectors so that takes out […]
11 January 2020
Baxi error code E133 – ignition lockout
E133 error code on a Baxi/ Potterton / Main boiler is an ignition lockout fault code. This error code that covers a wide range of possible faults connected to gas and igniton. In most cases you will need to contact a competent boiler repair engineer but there are some steps you can take yourself before […]