BlogRavenheat CSI 120 – hot water problems, hot water fluctuating between cold and hot
Ravenheat CSI 120 – hot water problems, hot water fluctuating between cold and hot
posted on 07 Mar 2015
This Ravenheat CSI 120 has been suffering with hot water problems. Hot water from the tap was fluctuating between hot and lukewarm. The reason for that was a blocked secondary heat exchanger. I have cleaned this exchanger about 3 months ago and suggested to the client that the system should be flushed to avoid the heat exchanger blocking again. The boiler has TF1 magnetic filter fitted on the return, but it seems that on very dirty systems it is not an adequate protection.
The course of action was to clean the system using suitable chemicals and Adey Magnacleanse system connected to return pipework to the boiler in place of TF1 filter. I prefer Adey Magnacleanse to power flushing as I find it more effective and quicker to do. You can read more about this system at Adey web site: Magnacleanse System. Below some pictures of sludge removed from the central heating. I like to clean the filters a few times during flushing to make sure they are more effective. This is what I got from about 2-3 radiators on this central heating system.
System got flushed and protected with suitable inhibitors (Sentinel X100). Once I got a nice and clean system water I cleaned and refitted TF1 filter and isolated the boiler. I then removed hot water heat exchanger to inspect it. As I suspected it was badly blocked on system water side. See picture below. The blocked port is on the right hand side and you can clearly see the blockage.
Next picture shows what comes out of a blocked heat exchanger if you tap it to remove the blockage. Please note that this is only a small part of blockage material that came out. I do not think it is possible to fully unblock a plate heat exchanger by tapping it alone. The best solution would be to replace it with a new one to avoid call backs. There are different methods of cleaning them with spirit of salts being the most popular one.
‘Plumber to fix leaking boiler in SE19’ – boiler repair blog
I got called to diagnose and repair a suspected boiler leak in SE19, Crystal Palace. The client actually used the phrase ‘Plumber to fix a leaking boiler in SE19’ to find me on Google. When I got to site I was met with this massive leak coming from the boiler pressure relief valve that has […]
12 January 2020
Vaillant Eco Tec ‘Con’ error code
If your boiler is showing ‘Con’ message on main display it means that your main PCB or possibly display PCB has failed and will need to be replaced. ‘Con’ message means that there is a communication error between main board and display board. Both boards are connected directly with pin connectors so that takes out […]
11 January 2020
Baxi error code E133 – ignition lockout
E133 error code on a Baxi/ Potterton / Main boiler is an ignition lockout fault code. This error code that covers a wide range of possible faults connected to gas and igniton. In most cases you will need to contact a competent boiler repair engineer but there are some steps you can take yourself before […]