Vaillant fault code F.76 is quite a worrying one. It means that main heat exchanger overheat protection had been activated. Vaillant Eco Tec range has a thermal fuse on top of the main heat exchanger that once activated breaks the circuit to prevent boiler from firing. That fuse is can not be reset and is not replaceable as once it is activated (at 140-160 degrees model dependable) main heat exchanger is deemed damaged beyond repair and must be replaced.
Before you go into panic mode though please be aware that this fault code may indicate a much less serious fault with wiring from the senor into the PCB. You will need a Gas Safe Registered heating engineer to confirm what had caused your Vaillant to show fault code F.76. Thermal fuse blowing and damaged heat exchangers are rare and in most cases this code points to a wiring issue. Unfortunately on my last repair with F.76 fault code the boiler main heat exchanger developed a leak combined with blocked pressure sensor. Sensor did not communicate to the boiler PCB that there was no pressure in the system and kept the burner on although there was no water in the heat exchanger. This in turn activated thermal fuse to prevent a catastrophic meltdown. Picture below shows a partially melted thermal fuse connector.
This is how the main heat exchanger looked inside.
Client decided to replace this 8 years old Vaillant 637 with a new one. Since all connections, flue and brackets were exactly the same the job was relatively straightforward and the boiler got replaced, system flushed and commissioned the same day. It is worth to note that the faulty boiler had never been serviced. New boiler came with 7 years warranty provided it is serviced annually. New boiler installed below.
‘Plumber to fix leaking boiler in SE19’ – boiler repair blog
I got called to diagnose and repair a suspected boiler leak in SE19, Crystal Palace. The client actually used the phrase ‘Plumber to fix a leaking boiler in SE19’ to find me on Google. When I got to site I was met with this massive leak coming from the boiler pressure relief valve that has […]
12 January 2020
Vaillant Eco Tec ‘Con’ error code
If your boiler is showing ‘Con’ message on main display it means that your main PCB or possibly display PCB has failed and will need to be replaced. ‘Con’ message means that there is a communication error between main board and display board. Both boards are connected directly with pin connectors so that takes out […]
11 January 2020
Baxi error code E133 – ignition lockout
E133 error code on a Baxi/ Potterton / Main boiler is an ignition lockout fault code. This error code that covers a wide range of possible faults connected to gas and igniton. In most cases you will need to contact a competent boiler repair engineer but there are some steps you can take yourself before […]